The machine should be carefully inspected before installing the intermediate frequency spot welder. After the welder has been transported or stored for a long time, the connection of all bolted joints must be carefully checked and all loose bolts and nuts must be tightened. The installation site should be free from corrosive, flammable and explosive gases, liquids, such as gasoline, to avoid fire. The following processes are also required:
1. Welding machine fixed
The installation position of the welder should not be ≤1.2 m from the wall to facilitate the maintenance of the welder and the heat dissipation of the welder. The welder should be fixed with the φ16X100MM anchor bolt. The anti-vibration rubber must be added during installation.
2. Gas source
The pressure of the air source should be stable, and the pressure of the compressed air should not be lower than 0.5Mpa. If necessary, the gas storage tank should be placed next to the machine, and the hose clamp should be clamped on the air intake three-component air inlet with the inner diameter φ12mm clamp hose.
3. Water source
The cooling water pressure is generally not lower than 0.15Mpa, and the inlet water temperature is not higher than 30 degrees. The water quality is required to be pure to reduce leakage or cause blockage of the pipeline. In places where there is multiple low-cost capacitor discharge welding machine china when the water source pressure is too low or unstable, a dedicated cooling water circulation system should be provided. The inlet and outlet connections are connected by a φ8mm mesh tube or water pipe.
4. Electrical installation
A. The electrical installation of the welder is required by a professional or an electrician’s license, and all the safety instructions and installation, operation and maintenance provisions in this manual should be familiar before using the equipment. Proper handling, handling, installation and operation, and maintenance are reliable guarantees for the safe and successful operation of this equipment.
B. The equipment body must be reliably grounded. The minimum cross-sectional area of the grounding conductor must be equal to or greater than the cross-sectional area of the power supply cable.
Address: Yuechang Hongtian Managerial Area, Xinxu Town, Huiyang, Huizhou, Guangdong, China.
Contact: Ms. Kary Hou
E-mail: [email protected]